The gas piping system shall be considered to be direct-bonded when permanently and directly connected to one of the following:
- the electrical service equipment enclosure
- the grounded conductor at the electrical service
- the grounding electrode conductor
- one or more of the grounding electrodes used
For single and multi-family structures, a single bond connection is made downstream of the individual gas meter for each housing unit and upstream of the first CSST connection. The bonding conductor should be no smaller than a 6 AWG copper wire or equivalent, and the bonding jumper should be attached in an approved manner in accordance with NEC Article 250.70. The point of attachment for the bonding jumper must be accessible. Bonding/grounding clamps shall be installed in accordance with its listing per UL 467 and need to make metal-to-metal contact with a steel pipe component or the first CSST fitting. This bonding requirement is in addition to any other bonding requirements that are specified by local codes.
The CSST portion of the gas piping system must not be used as the point of attachment of the bonding clamp at any location along its length under any circumstances.